Download American Standard Gas Furnaces User's Manual for Free
Download Furnace User's Manual of American Standard Gas Furnaces for free from ManualAgent.
Gas Furnaces — Non-Condensing
Fan Assisted Combustion System
Upflow / Horizontal and Downflow / Horizontal
User’s Information Guide
DO NOT USE THIS UNIT IF ANY PART HAS BEEN UNDER
WATER. IMMEDIATELY CALL A QUALIFIED SERVICE
TECHNICIAN TO INSPECT THE FURNACE AND TO RE-
PLACE ANY PART OF THE CONTROL SYSTEM AND ANY
GAS CONTROL WHICH HAS BEEN UNDERWATER.
Understand the signal words DANGER, WARNING, AND
CAUTION. These words are safety alert words. DANGER
indicates the most serious hazards which
will result in
severe personal injury or death. WARNING indicates hazards
could result in personal injury or death. CAUTION is
used to indicate unsafe practices which could result in minor
injury or property damage.
Dangers, Warnings & Cautions 1
General Information 1
To Start the Furnace 2
Proper Maintenance 4
The Problem Solver 6
Regular Dealer Maintenance 7
If the information in this manual is not followed exactly,
a fire or explosion may result causing property
damage, personal injury or loss of life.
— Do not store or use gasoline or other flammable
vapors and liquids in the vicinity of this or any
— WHAT TO DO IF YOU SMELL GAS
• Do not try to light any appliance.
• Do not touch any electrical switch;
do not use any phone in your building.
• Immediately call your gas supplier from a
neighbor’s phone. Follow the gas supplier’s
• If you cannot reach your gas supplier,
call the fire department.
— DO NOT RELY ON SMELL ALONE TO DETECT
LEAKS. DUE TO VARIOUS FACTORS, YOU MAY
NOT BE ABLE TO SMELL FUEL GASES.
• U.L. recognized fuel gas and CO detectors are
recommended in all applications, and their
installation should be in accordance with the
manufacturer's recommendations and/or local
laws, rules, regulations, or customs.
— Installation and service must be performed by a
qualified installer, service agency or the gas
The flow of combustion and ventilating air must not be
obstructed from reaching the furnace. Air openings provided
in the casing of the furnace must be kept free of obstructions
which would restrict airflow, thereby affecting efficiency and
safe operation of your furnace.
Also, air openings provided to the area in which the furnace
is installed and the space around the furnace shall not be
blocked or obstructed. Keep this in mind should you choose to
remodel the area which contains your furnace. If additional
insulation is added after the furnace is installed, the area
around the furnace must be inspected to ensure it is free and
clear of insulation. If this furnace is installed in an attic or
other insulated space it must be kept free and clear of all insu-
lating materials as some insulating materials are combustible.
Furnaces must have air for proper performance. There must
be a free flow of fresh air sufficient for efficient combustion
and safe ventilation of your furnace.
The combustion air for your furnace must be fresh uncon-
taminated air. Paints, varnishes, laundry bleaches, deter-
gents, many household cleaners, water softening salts,
adhesives, and all such products release fumes containing
compounds which could lead to early heat exchanger and
vent system deterioration. Do not store these types of
products near your furnace.
Never store gasoline, combustible materials, or other flam-
mable liquids or vapors near your furnace.
Carbon monoxide, fire or smoke can cause serious bodily
injury, death, and/or property damage.
Related Manuals for American Standard Gas Furnaces
American Standard Furnace Gas Furnaces Manual
User's Manual: (12 pages)
Bryant Furnace PLUS 90X 353AAV Manual
User's Manual: (22 pages)
Bryant Furnace 310AAV Manual
Service Manual: (45 pages)
Bryant Furnace 395CAV Manual
User's Manual: (8 pages)
Bryant Furnace 915SA Manual
Product data: (16 pages)
Bryant Furnace 350MAV Manual
User's Manual: (12 pages)
Bryant Furnace PLUS 95S 355CAV Manual
Owner's Manual: (14 pages)
Carrier Furnace 58PAV Manual
User's Manual: (16 pages)
Carrier Furnace Deluxe 58MVP Manual
Troubleshooting: (48 pages)
Carrier Furnace WEATHERMAKER 8000 58ZAV Manual
Instruction Manual: (24 pages)
Coleman Furnace DGAA Manual
User's Manual: (14 pages)
Coleman Furnace EB12B Manual
Installation Manual: (20 pages)
De'Longhi Furnace DRAGON 3 Manual
Instruction Manual: (6 pages)
Ducane Furnace FITS-ALL 92 Manual
Specifications: (4 pages)
FIELD CONTROLS Furnace 46334200 Manual
Instruction Manual: (20 pages)
Goodman Mfg Furnace GMH95 Manual
User's Manual: (15 pages)
Goodman Mfg Furnace GMS90453BXA Manual
Parts list: (11 pages)
Rheem Furnace CRITERION II Manual
Installation Manual: (8 pages)
Rinnai Furnace RHFE-263FA II Manual
Owner's Manual: (44 pages)
Trane Furnace XR 90 SERIES Manual
Owner's Manual: (16 pages)
United States Stove Furnace 1357M Manual
Owner's Manual: (28 pages)
United States Stove Furnace 2941 Manual
Owner's Manual: (10 pages)